What is Goose in IEC 61850?
GOOSE (IEC 61850) The GOOSE (Generic Object Oriented Substation Event) protocol is a communication model defined by the IEC 61850 standard, which uses fast and reliable mechanisms to group any format of data (status, value) into a data set and transmit it across communication networks within 4 milliseconds.
What does the industry standard IEC 61850 cover?
IEC 61850 is an international standard defining communication protocols for intelligent electronic devices at electrical substations. These protocols can run over TCP/IP networks or substation LANs using high speed switched Ethernet to obtain the necessary response times below four milliseconds for protective relaying.
What is Goose configuration?
Generic Object Oriented Substation Events (GOOSE) is a controlled model mechanism in which any format of data (status, value) is grouped into a data set and transmitted within a time period of 4 milliseconds.
What are goose messages?
GOOSE messages are “published” by a device via Ethernet multicast such that they can be “subscribed” by any number of other devices. These messages are based on datasets. A change in value of any dataset member is considered a change of “state”, the new information is published immediately.
How does goose protocol work?
GOOSE protocol is an event-based protocol. The concept of GOOSE communication is that the publisher periodically sends messages and when an event happens (ex. Trip, Contactor closed …), it sends a burst of messages with new data.
How do you read IEC 61850?
IEC 61850 defines a fast and reliable point to multi point message exchange procedurethat can be used to replace copper wiring using in the data exchange between the cabinets in a substation. These messages are called GOOSE – Generic Object Oriented Substation Event.
How does a goose work?
GOOSE messages are “published” by a device via Ethernet multicast such that they can be “subscribed” by any number of other devices. These messages are based on datasets.
What is Goose testing?
IEC 61850 GOOSE messaging is widely used for the real-time communication of status information within Digital Substations (e.g. pickup or trip). With GOOSE, the formerly hard-wired binary signals are distributed throughout the network efficiently.
What is Goose engineering?
Goose Engineering is an engineering company, with national and international partnerships, that seeks to deliver a complete solution to its customers.
How do I use the IEC 61850/Goose feature?
To use the IEC 61850 / GOOSE feature, you need to enable real-time networking. It is disabled by default, as of Version 2.04, because on rare occasions it prevents the FTP and HTTP servers from working with certain network configurations. It’s easy to disable later, if there’s a problem, so enabling it is risk-free.
What is the best IEC 61850 tool?
IEC 61850 Substation Configuration Tool The ASE61850 SCL Manager is the leading IEC 61850 Substation Configuration Tool (SCT) in the market. This tool supports Edition 1.0 and Edition 2.0 and is continuously updated to comply with the changes in the standard. 50% OFF for ASE2000 Customers.
What are the features of IEC 61850 Substation Configuration Tool?
• SCL- XML editor. IEC 61850 Substation Configuration Tool allows the user to edit the corresponding XML file (SSD) generated when the user draws the elements in SLD. • Tag Generator. Users can create communication tags for the SCD file which can be stored in the file.
What is ase61850 SCL manager?
The ASE61850 SCL Manager is the leading IEC 61850 Substation Configuration Tool (SCT) in the market. This tool supports Edition 1.0 and Edition 2.0 and is continuously updated to comply with the changes in the standard. 50% OFF for ASE2000 Customers. Use PROMO CODE: I-HAVE-ASE2000